Home / Store / Journals / Electronic Articles / Nuclear Technology / Volume 176 / Number 2
J. Blázquez, I. Vallejo, A. García-Berrocal, M. Balbás
Volume 176 / Number 2 / November 2011 / Pages 284-289
Format:electronic copy (download)
In the case of large burnup, a control rod (CR) guide tube in the pressurized water reactor of a commercial nuclear power plant might bend. As a consequence, a CR drop experiment may indicate an event of a CR partially inserted and whether the CR should be deemed inoperable. Early prevention of such an event can be achieved by measuring two friction coefficients: the hydraulic coefficient and the sliding coefficient. The hydraulic coefficient hardly changes, so that the curvature of the guide tube can only be detected thanks to a variation of the sliding coefficient. A simple model for the CR drop is established and validated with CR drop experiments. If tmx denotes the instant of CR maximum velocity, a linear relationship between (tmx)-2 and the sliding coefficient is found.
Your cart is empty.
Home|Invoice Payment|Nuclear Links