Home / Store / Journals / Electronic Articles / Nuclear Technology / Volume 172 / Number 2 / Pages 101-107
Nuclear Technology / Volume 172 / Number 2 / Pages 101-107
Format:electronic copy (download)
Some 400 boiling water reactors (BWRs) and pressurized water reactors (PWRs) have been in operation for several decades. The presented concept, the high pressure boiling water reactor (HP-BWR), combines the best parts and omits the troublesome components of traditional BWRs and PWRs by taking into consideration the experiences gained during their operation.One of the major benefits of the HP-BWR is that safety is improved. The design utilizes gravity-operated control rods, and there is a large space for the cross-formed control rods between fuel boxes. The bottom of the reactor vessel is smooth and without penetrations. All the pipe connections to the reactor vessel are well above the top of the reactor core, and core spray is not needed. Additionally, internal circulation pumps are used.The HP-BWR concept is also environmentally friendly: Improved thermal efficiency is achieved by feeding the turbine with [approximately]340°C (15 MPa) steam instead of [approximately]285°C (7 MPa), and there is less warm water release to the recipient and less uranium consumption per produced kWh, resulting in the production of less waste.Finally, the HP-BWR is cost effective and simple, operating in direct cycle mode with no need for complicated steam generators. Moisture separators and steam dryers are placed inside the reactor vessel, and additional separators and dryers can be installed inside or outside the containment. Well-proved simple dry containment or wet containment can be used.In more than half a century, an extensive regulatory licensing experience has been built from traditional BWRs and PWRs. The HP-BWR is a developed, high-performance successor of those conventional designs. Therefore, it can be expected that licensing can be accomplished in a reasonable time.Several utilities are supporting manufacturers to study concepts for future reactors. It is likely that an application to one or more electrical power companies for financial support by a manufacturer to make a detailed feasibility study of the HP-BWR would be positively treated. This could be the next step to the implementation of the HP-BWR.
Your cart is empty.
Home|Invoice Payment|Nuclear Links